In order to ensure the normal operation of Shandong gas-fired boiler, you know about the function and safety maintenance of gas-fired boiler. Let Jinan Lianzhong heating equipment factory take you to have a deep understanding of gas-fired boiler!
在小型燃气锅炉的运转中严禁在没有水或水的情况下熄灭，以免发作事故。假定发现小型燃气锅炉严重缺水，应立即中止供暖。 小型燃气锅炉冷却后，找出缘由并扫除缺陷。 不要加水以防止炉子损坏。
In the operation of small gas-fired boiler, it is strictly prohibited to extinguish without water or water, so as to avoid accidents. If the small gas-fired boiler is found to be seriously short of water, the heating should be stopped immediately After the small gas boiler is cooled, find out the reason and remove the defect Do not add water to prevent damage to the furnace.
小型燃气锅炉的操作人员熟练控制小型燃气锅炉的性能，操作程序和工艺流程，以防止非法操作。 当炉子在冬天关闭时，排出锅炉水以防止小型燃气锅炉冻结。 在夏季不运用小型燃气锅炉时，应将锅炉水排干，并用石灰中止单调维护。
The operators of small gas-fired boiler shall be skilled in controlling the performance, operation procedure and process flow of small gas-fired boiler to prevent illegal operation When the furnace is shut down in winter, discharge the boiler water to prevent the small gas boiler from freezing When the small gas-fired boiler is not used in summer, the boiler water shall be drained and the monotonous maintenance shall be stopped with lime.
假定发现小型燃气锅炉的吸力减小，则应清洁炉子，并应用颈部或烟囱门内的橡胶软管清洗自来水。 小煤气锅炉除垢可在运用1年后开启，观察沙井的水垢厚度，加上除垢剂除垢，还可参与5-10kg烧碱或盐酸和水煮24炉。 -36h，除垢和洗濯炉。 根据当地的水质，每六个月中止一次清洁操作，以去除小型燃气锅炉的水垢。 否则，对流管容易结垢，招致对流管堵塞和烧坏。
If it is found that the suction of small gas-fired boiler is reduced, the furnace shall be cleaned and the tap water shall be cleaned with a rubber hose in the neck or in the chimney door The scale removal of small gas boiler can be started after one year's operation. Observe the scale thickness of the sand shaft, add the scale remover to remove the scale, and participate in 24 boilers of 5-10kg caustic soda or hydrochloric acid and boiling water -36h, descaling and washing stove According to the local water quality, the cleaning operation shall be stopped every six months to remove the scale of small gas-fired boiler Otherwise, the convection pipe is easy to scale, resulting in blockage and burning of the convection pipe.
Gas-fired boilers are mainly used for heating and bathing in industries such as chemical industry, pharmacy, paper making, printing and dyeing, food, packaging, foam, hospitals, hospitals, schools, hotels, houses, etc. Inform you of precautions for gas boiler installation.
1. The gas boiler shall not be installed in the bedroom or the room directly connected with the bedroom, and shall not be installed in the open room where the air is not smooth.
2.燃气锅炉电源运用220V / HZ交流电源，衔接可靠的接地导线，以确保安全运用。
2. The power supply of gas boiler shall be 220V / Hz AC power supply, and reliable grounding wire shall be connected to ensure safe operation.
3. Special gas pipeline shall be used for connection between gas pipeline and gas extinguisher.
4. After installing the gas pipeline, turn over the gas valve and check whether there is soap liquid in the connecting part Assuming disclosure, close the valve to repair or replace the seal, then check the gas boiler until no disclosure.
5. The boiler installation shall be flat or reasonably designed to be as short, few and thick as possible, that is to say, the pipe shall be shortened as much as possible and the bending shall be reduced, and the pipe diameter shall be thick.
6.自然循环中主管道的坡度和回水管道的坡度为3-5％。 不应构成波浪以防止管道中的气体堵塞。 管道系统中的排气管应放置在系统的较高点，不应安装阀门。
6. The gradient of main pipeline and return pipeline in natural circulation is 3-5% Waves shall not be formed to prevent gas blockage in the pipe The exhaust pipe in the pipeline system shall be placed at the higher point of the system, and the valve shall not be installed.
7.将排水阀安装在系统的较低点。 供水箱底部应高于供水管的较高点。 出风口不应由自动排气阀替代。 阀门不应安装且不应堵塞。
7. Install the drain valve at the lower point of the system The bottom of the water supply tank shall be higher than the higher point of the water supply pipe The air outlet shall not be replaced by automatic exhaust valve Valves shall not be installed and blocked.
8，燃气锅炉系统管道长，弯曲道路多，无坡度，加热效果不好。 应安装循环泵。 水泵应安装在供水管道上，泵的尺寸应根据加热面积选择。
8. The gas boiler system has a long pipeline, many curved roads, no slope, and poor heating effect Circulating pumps shall be installed The water pump shall be installed on the water supply pipeline, and the size of the pump shall be selected according to the heating area.
9. When installing the pipeline, it shall extend outwards with a slope of 5 ° downward to prevent the condensate from moving backward, forming the corrosion of the furnace body, and there is no inflammable substance around the pipeline.
The above is the introduction of Jinan Lianzhong heating equipment plant to gas boiler. For more information, please click http://www.jnlzsb.com